X800 Fast Acting CleanerClean
Rapid cleaner for systems older than six months and powerflushing
A heavy-duty, multi-purpose cleaner, Sentinel X800 Fast Acting Cleaner quickly removes corrosion deposits and scale from older systems. Developed especially for use with powerflushing machines to provide a more rapid and effective clean, it restores circulation to old, dirty heating systems and prepares new systems for the addition of Sentinel X100 Inhibitor.
- Powerful removal of all major foulants and debris
- Cleans rapidly even in cold systems
- Ideal with or without powerflushing
- Exceptional result when powerflushing
- Harmless to the environment, completely non-toxic and biodegradable
- Suitable for use with all commonly encountered metals and alloys
Sentinel X800 Fast Acting Cleaner restores a more even heat distribution to old systems, keeping the house warmer and bills lower.
Sentinel X800 Fast Acting Cleaner uses TripleTech™ Power Clean Technology, a unique formula with 3 different chemical technologies, to penetrate, attack and dissolve corrosion debris and limescale into a 'ready to flush' solution. In addition to its cleaning properties, X800 Fast Acting Cleaner also provides temporary anti-corrosion protection, preparing systems for the addition of Sentinel X100 Inhibitor.
The unique composition of X800 Fast Acting Cleaner allows it to work under neutral pH conditions, eliminating the concerns associated with conventional acid cleaners.
1 litre of Sentinel X800 Fast Acting Cleaner is sufficient to clean a typical system of up to 10 radiators. For larger systems, 2 litres should be used. Where systems are badly fouled, a higher concentration is recommended, i.e. 2 litres for a typical system. This product will not clear a completely blocked pipe.
To clean an older system in accordance with BS 7593it is recommended that this product is used with powerflushing equipment. In this scenario, administer Sentinel X800 JetFlo Ultimate Cleaner via the powerflushing equipment, following equipment manufacturer's instructions. Alternatively, circulate the product (preferably at normal operating temperature, with all valves open and the pump turned to maximum flow) for a minimum period of 1 hour or until satisfactory performance is restored.
Powerflushing: Follow the instructions supplied with the powerflushing machine.
Open Systems: Dose via F&E cistern, via a by-pass feeder or use a Sentinel Dosing Vessel.
Sealed Systems: If the system is empty, add to any convenient point before filling. If full, use
a Sentinel Dosing Vessel to inject via the filling loop or other access point.